Kent Fire Department
Internationally Accredited Fire Agency
Location: 400 W. Gowe St.
Mail to: 220 4th Avenue South
Kent, WA 98032-5895
Office: 253-856-4400 ∙ Fax: 253-856-6400
Serving the Cities of Kent, Covington and King County Fire District 37
Indoor Container Storage
Please print in black ink only.
This checklist pertains to the design and
construction of facilities where containers of
hazardous materials in excess of the exempt Yes No
amounts are stored indoors in industrial, fac- Owner’s name, address, telephone
tory, manufacturing, educational or similar uses. number.
Minimum Requirements for Occupant’s name, address, telephone
Construction Drawings number, if different from owner.
Contractor’s name, address, fax number,
Plans which do not contain the minimum infor- telephone number and Washington State
mation required will not be accepted for plan check. Contractor’s license number.
Plans shall be of sufficient clarity to indicate the
location, nature and extent of the work proposed Documentation—One Set
and show that it will conform to the provisions of the Yes No
adopted International Codes and ordinances.
Type of construction and occupancy
Three (3) copies of plans (24" x 36", or 30" x 42") classification of building.
must be submitted for review. Description and quantity of material to
Copies shall all be the same size. be stored, including container size
Working Drawings – scale to 1/8" = 1'. and type.
Shall be drawn in indelible ink. Completed Fire Department Chemical
Sheets that are cut and pasted, taped, or that Inventory Material, Safety Data Sheets
have been altered by any means (pen, pencil, (MSDS) and Hazardous Materials
marking pen, etc.) will not be accepted for Management Plan (HMMP).
Fire sprinkler system design and instal-
Site Plans – scale to 1" = 20' or 1" = 40' lation details.
Washington State law requires that any regis-
tered professional who prepares or supervises Design and sample hazardous materials
the preparation of drawings and construction warning signs.
documents stamp and sign such documents. Sample storage plan showing arrange-
ment, location and dimensions of aisles.
Design and construction details on carts
and powered industrial trucks used for
RH1-1 fpd3011 2/17/06 p. 1 of 2
Working Drawings Make, model, type and design of emer-
Yes No gency alarm and fire detection systems.
Site plan scale 1" = 20' or 1" = 40', floor Make, model, method and design of gas
plan and full height cross section of storage, treatment and detection systems.
building, including smoke venting. Make, model, method and design of
Floor plan detail showing specific loca- exhaust scrubber systems.
tion where storage or handling will occur Note:
and area/occupancy separations, control
areas, aisles, storerooms, floor open- Spill control in flammable liquid use, dispensing and
ings, exits and heating, ventilation and mixing rooms is to prevent spilled liquids from flow-
air conditioning systems. ing out of the room.
Location, area, height, detailed design Drainage control in flammable liquid use, dispens-
and seismic analysis of shelves or racks. ing and mixing rooms is achieved by piping spilled
liquids and fire protection water to an approved lo-
Method used to achieve spill control, cation or treatment system with overflow protection,
drainage control and secondary contain- or by providing secondary containment.
ment, and its termination point.
Secondary containment in flammable liquid use,
Design and installation details of over- dispensing and mixing rooms is achieved by piping
flow protection from secondary spilled liquids and fire protection water to an ap-
containment. proved location or containment system, or by sizing
Location and rating of portable fire pro- the spill control to provide adequate containment
tection equipment, including fire and is provided with overflow protection.
extinguishers. PlEASE READ ThE iNfORMATiON bElOW
Detailed designs and location of hazard- AND SiGN bEfORE SubMiTTiNG YOuR
ous materials storage or gas cabinets. APPliCATiON
Location, make, model and type of leak Your application shall be deemed complete only if
detection or monitoring equipment. this checklist is completed and submitted along with
the submittal package. Submittals not accompanied
Detailed designs and equipment to pro-
by a checklist will not be accepted. Accuracy of the
vide continuous mechanical or natural
submittal package, including this checklist, is the
ventilations, including interlocks, emer-
responsibility of the applicant. Failure to submit an
gency and manual overrides.
accurate submittal package will be considered an
Make, model and classification of electri- incomplete application by the Plan Reviewer. An
cal wiring and equipment. incomplete submittal will result in a HOLD. A Re-
submittal (new submittal package) will be required
Method to protect materials from static
and always results in a delay.
electricity, light and shock.
Method(s) to separate incompatible haz- I have checked the applicable boxes and have
ardous materials. included those requirements in my submittal.
Method and detailed engineering calcu-
lations to provide explosion control.
Make, model, type and rating of standby Print Name
power equipment, including operational
sequence and wiring diagram.
Make, model, type, rating and capacity Signature
of liquid limit level, pressure and tem-
perature limit control.
RH1-1 fpd3011 2/17/06 p. 2 of 2