VIEWS: 12 PAGES: 6 CATEGORY: Medicine POSTED ON: 5/28/2010
The fire protection codes being used include the 2000 editions of the International Building Code (IBC) and the International Fire Code; the 1999 edition of NFPA 13, Installation of Sprinfeler Systems; the 2000 edition of NFPA 14, installation of Standpipes and Hose Systems; the 1999 edition of NFPA 20, installation of Stationary Pumps for Fire Protection; the 1995 edition of NFPA 24, Installation of Private Fire Service Mains and Their Appurtenances; the 2002 edition of NFPA 415, Airport Terminal Buildings, Fueling Ramp Drainage, and Loading Walkways; and the 1994 edition of NFPA 2001, Clean Agent Fire Extinguishing Systems. Fire extinguishers are provided in each retail space, within 30 feet (9 meters) of all the commercial cooking equipment, and in each storage, maintenance, mechanical, and electrical equipment room.\n A preaction system is also used for the water curtain at the entrance to the terminal from the pedestrian bridge at the Departures level, which links the parking garage to the terminal.
Pages to are hidden for
"WATER-BASED SUPPRESSION FOR THE New Indianapolis Airport"Please download to view full document