"SymmetrE R310 1 Service Pack 1 SP1"
Software Release Bulletin August 17, 2006 Issue 2 SymmetrE R310.1 Service Pack 1 (SP1) This document provides important information about release contents and installation procedures. It assumes you are already familiar with the previous releases of SymmetrE. This article discusses: It applies to: • New or changed functionality SymmetrE R310.1 • Localization • Installation • List of deliverables • Resolved Issues Related documents: Support: • SymmetrE R310.1 Software Release Bulletin For information about updates to this bulletin, contact your nearest Honeywell • SymmetrE R310.1 Localization Toolkit Guide office or Technical Assistance Center. This document contains Honeywell proprietary information. Information contained herein is to be used solely for the purpose submitted, and no part of this document or its contents shall be reproduced, published, or disclosed to a third party without the express permission of Honeywell International. HONEYWELL DISCLAIMS THE IMPLIED WARRANTIES OF MERCHANTABILITY AND FITNESS FOR A PURPOSE AND MAKES NO EXPRESS WARRANTIES EXCEPT AS MAY BE STATED IN ITS WRITTEN AGREEMENT WITH AND FOR ITS CUSTOMER. In no event is Honeywell liable to anyone for any direct, special, or consequential damages. The information and specification in this document are subject to change without notice. Revision status Version Date Description 1 16 August 2006 Initial version. 2 17 August 2006 Updated after internal review Revision description 2 www.honeywell.com Contents New or changed functionality 4 Installing the software 6 Localization 6 Notes about installing the service pack 6 Prerequisites 6 For a new installation or existing SymmetrE R310.1 system 7 List of deliverables 8 Product deliverables 8 File list 8 Resolved issues 10 Problems resolved since SymmetrE R310.1 10 Problems resolved in HMIWeb Station and Display Builder R3.5 Build 390 11 Problems resolved in SymmetrE Web Server R3.5 Build 390 11 Problems resolved in Quick Builder R2.30 Build 1131 11 Appendices 12 Appendix A – ActiveX controls embedded in DSP and HMIWeb display pages 12 www.honeywell.com 3 New or changed functionality Platform Support Support for Microsoft Internet Explorer ActiveX update MS06-013: Cumulative Security Update for Internet Explorer (KB 912812). Changes include: • ISR67887: DSP pages and all other ActiveX controls require double-clicking to load in SymmetrE Web Server (ActiveX hotfix). • ISR68393: Microsoft is changing the way ActiveX controls are loaded on HTML pages. SymmetrE system displays need modification to avoid the new behavior. • ISR68587: Print/Print preview will cause the DSP page to require activation again in SymmetrE Web Server (ActiveX hotfix). Refer to Appendix A – Changes to the behavior of ActiveX controls embedded in DSP and HMIWeb display pages. BACnet Direct Client ER5682: BACnet Workstation Enhancement Phase 1 which includes the following. BACnet Point Server • ISR49885: Cannot read object list from devices that do not support segmentation if it is larger than one segment. Need to read these object lists one object at a time. • ISR63078: Cannot read object list from devices that contain more than 1000 objects. • ISR63088: If a device does not support the AddListElement service, the BACnet Point Server should use the WriteProperty service to modify the Recipient_List property of Notification Class Objects. • ISR64062: Cannot reset elapsedactivetime (runtime counter) because property is marked as read-only. Quick Builder • ISR57695: The list of discovered devices should be sorted alphabetically. • ISR63076: The Who-Is delay should be configurable for the BACnet Discovery Wizard to allow for slower devices to respond. • ISR65751: BACnet Direct point component has 'Event Enrollment' object spelt as 'Event Enrolment'. • ISR68147: BACnet Discovery Wizard controller fields should be adjustable and sortable. • ISR68148: The BACnet Discovery Wizard should show the discovered device instances in the controller list. System Displays • ISR63854: Runtime counter elapsedactivetime on BACnet Binary Output and Value objects should be displayed in HH:MM. • ISR67945: Units are missing for Minimum on time and Minumum off time on BACnet Binary Output and Value objects. GDA Notification Client • ISR68518: Alarms are generated on points that are not engineered in the SymmetrE server database. For some large installations this is an issue. 4 www.honeywell.com EXCEL 5000 Direct ER5768: Excel 5000 Direct needs to support configurable XL50 controllers (i.e. with fixed applications). SymmetrE Web Server ER5470: SymmetrE Web Server needs an automated upgrade mechanism. www.honeywell.com 5 Installing the software This section is intended for people who will install this service pack. Localization New SymmetrE R310.1 Service Pack 1 localization disks are required for this service pack. Contact your regional affiliate. Notes about installing the service pack • A service pack is a special cumulative update. Service Pack 1 is Cumulative Update 3. • The Service Pack 1 installation package backs up any existing files that are to be updated by this package. This is done by copying the original file with the same name and appending .precu3. • If a .precu3 backup already exists (for example, if Service Pack 1 is installed multiple times) the existing file is not overwritten and the new files installed for the first time will be backed up with the.precu3 extension. • Service Pack 1 does not overwrite files with a newer file version. If the versions are the same, the file will be overwritten. • If the file delivered does not contain file version information, then the file date/time is used. • You can start installing Service Pack 1 with the server running or stopped. The Service Pack 1 installation stops the SymmetrE Server, Lonworks Point Server, EXCEL 5000 Direct (Point Server), BACnet Direct Client (Point Server) and Networked XLNET Node (NXN). • This service pack includes updated Station and Quick Builder. You must install the service pack on computers other than the SymmetrE Server where these components are installed. • This service pack includes changes for Lonworks Point Server, Excel 5000 Direct (point server), BACnet Direct Client (Point Server) and Networked XLNET Node. You must install the service pack on computers other than the SymmetrE Server where these components are installed. • Do not directly run setup programs in any \server subfolders. This can cause the installation to fail and the system may become unstable. You should always run the main setup.exe located in the \server folder. Prerequisites Before installing this service pack: • Important: As a precaution, you should always back up your system before installing this service pack. It is recommended you use a program like Norton Ghost or Acronis to take an image of the hard drive partition where Windows is installed and where SymmetrE is installed (which may be the same partition). Norton Ghost does not support RAID drives. • Install SymmetrE R310.1 Build 32.6. • If you have recently installed or uninstalled any software on the server, including Honeywell products, and have not restarted the server, you must restart the server before installing this service pack. • Close all running applications including: The Start/Stop SymmetrE Server utility Any third-party applications or software that access SymmetrE 6 www.honeywell.com Point servers other than Lonworks Point Server (LPS), EXCEL 5000 Direct (Point Server) and BACnet Direct Client (Point Server) • If the server has been stopped and started (for example, after a backup), allow it to run for at least five minutes after going to “System Running”. This allows tasks run at startup to complete before the service pack is installed. For a new installation or existing SymmetrE R310.1 system Server To install the service pack on a server: 1 Log on to the server computer as a user that is a member of Administrators and Honeywell Administrators group. 2 Run the setup program \Setup\setup.exe from the CD. 3 Follow the on-screen prompts and wait for the installation to complete. 4 At the end of the installation process, restart the computer if requested. Client (Station and Quick Builder) To install the service pack on a client: 1 Log on to the computer as user that is a member of the Administrators group. 2 Run the setup program \Setup\setup.exe from the CD. 3 Follow the on-screen prompts and wait for the installation to complete. 4 At the end of the installation process, restart the computer if requested. Point Server (Lonworks, Excel 5000 Direct, BACnet Direct Client) and Network XLNET Node (NXN) To install the service pack: 1 Log on to the computer as user that is a member of the Administrators group. 2 Run the setup program \Setup\setup.exe from the CD. 3 Follow the on-screen prompts and wait for the installation to complete. 4 At the end of the installation process, restart the computer if requested. www.honeywell.com 7 List of deliverables Product deliverables The following is a list of the physical product deliverables for Enterprise Buildings Integrator R310.1. Item Build/Issue Media Part Number Service Pack 1 for SymmetrE SymmetrE R310.1 SP1 CD ZP41-SYM310.1-CD4 R310 ROM Station R3.5.544.390 (Included on CD) HMIWeb Display Builder R3.5.544.390 (Included on CD) SymmetrE Web Server R3.5.544.390 (Included on CD) Quick Builder R2.30.802.1131 (Included on CD) File list The following files are included in this service pack. Where version information is not available for a file, the file size and creation date/time is provided. File Name Windows File Version Modified Date/Time Size (bytes) acrnym_vinps.src unknown 14/02/2006 10:42 73 acscfg.exe 7184.108.40.206 22/02/2006 11:48 1462334 acskey.src unknown 13/02/2006 14:26 23083 bac_d.exe 7220.127.116.11 22/03/2006 15:41 913469 bacacc.dll 18.104.22.168 03/11/2003 14:10 159811 baccli.dll 22.214.171.124 03/11/2003 14:08 217157 bacgtw.dll 126.96.36.199 03/11/2003 14:11 266309 bacosa.dll 188.8.131.52 03/11/2003 14:06 81984 bacsrv.dll 184.108.40.206 03/11/2003 14:09 262213 bacutil.dll 220.127.116.11 03/11/2003 14:06 77891 cbnobj.exe unknown 03/11/2003 14:10 102467 bacnetinfo.dll 718.104.22.168 23/03/2006 17:13 32842 BacNetPointServer.exe 300.2.0.30 21/03/2006 10:05 266335 dsply.exe 722.214.171.124 22/03/2006 15:13 1458237 gdamngr.exe 7126.96.36.199 31/03/2006 12:25 786495 GdaNotCli.exe 7188.8.131.52 20/03/2006 9:17 950337 Honeywell Logger Service.msi unknown 8/12/2005 13:12 313344 HSCTableCursor.dll 7184.108.40.206 22/03/2006 13:06 1237062 8 www.honeywell.com HWSystemDSAReplication.sql unknown 22/02/2006 19:43 71 ItemDetails.htm unknown 3/04/2006 9:24 30762 ItemDetails_activex.vbs unknown 31/03/2006 13:37 269 licdspacr.exe 7220.127.116.11 30/03/2006 12:49 593985 licdspacr.exe 718.104.22.168 30/03/2006 12:49 593985 licenter.exe 722.214.171.124 30/03/2006 12:49 573504 lichange.exe 7126.96.36.199 30/03/2006 12:49 606272 licheck.exe 7188.8.131.52 30/03/2006 12:49 593983 licinstall.exe 7184.108.40.206 30/03/2006 12:49 602178 liclist.exe 7220.127.116.11 30/03/2006 12:49 610367 QAGLayouts.xml unknown 28/04/2006 14:05 12288 QBinf780_310.dll 718.104.22.168 04/05/2006 17:24 589888 salt.exe 22.214.171.124 24/03/2006 15:43 340019 slgscn.exe 7126.96.36.199 22/02/2006 17:03 892990 StationMessages.txt unknown 27/03/2006 18:27 34419 sysCfgGtsDetail.htm unknown 31/03/2006 12:25 253406 sysCfgGtsDetail_activex.vbs unknown 31/03/2006 12:28 455 sysCfgPntSrv.dsp unknown 2/05/2006 11:48 13070 sysDtlBacNetBI.dsp unknown 17/03/2006 8:55 12767 sysDtlBacNetBO.dsp unknown 17/03/2006 8:55 15395 sysDtlBacNetBV.dsp unknown 17/03/2006 8:55 13818 sysdtlbacnetsch.htm unknown 3/04/2006 9:01 39884 sysdtlbacnetsch_activex.vbs unknown 31/03/2006 12:33 1050 sysdtlbacnetschexceptionmodify.htm unknown 3/04/2006 9:07 322209 sysdtlbacnetschexceptionmodify_activex.vbs unknown 31/03/2006 12:33 1112 sysdtlbacnetschweekly.htm unknown 3/04/2006 9:12 343452 sysdtlbacnetschweekly_activex.vbs unknown 31/03/2006 12:33 1100 sysdtlxl5remotebus.htm unknown 3/04/2006 9:17 64729 sysdtlxl5remotebus_activex.vbs unknown 31/03/2006 13:24 3388 sysLicenceInter.dsp unknown 17/01/2006 14:12 6949 syssummaryxl5dusites.htm unknown 3/04/2006 9:19 12775 syssummaryxl5dusites_activex.vbs unknown 31/03/2006 13:23 1765 ulpscn.exe 7188.8.131.52 22/02/2006 17:07 872510 UpdateSlogger.vbs unknown 4/04/2006 13:40 3316 upgradecms.sql unknown 22/02/2006 16:47 85153 xl5ps.exe 7184.108.40.206 24/04/2006 17:47 835655 xlsdmn.exe 7220.127.116.11 16/02/2006 13:50 618558 www.honeywell.com 9 Resolved issues The following problems have been resolved in SymmetrE R310.1 SP1. Problems resolved since SymmetrE R310.1 Alarm/Event Presentation • ISR55557: The Area filter description on the alarm summary sometimes shows the incorrect area filter name. BACnet Direct Client (Point Server) • ISR63026: With Auto discovery disabled, and all areas disabled, notifications are still generated but with the system area. • ISR70366: BACstac files delivered on a standalone BACnet Point Server are the wrong version. BACnet Server • ISR64346: Read property errors can cause BACstac to run out of resources and halt. • ISR66799: BACnet Server returns error code 'other' if properties are not mapped. Display Subsystem • ISR64695: Cannot control points from the alarm line of an alarm instruction page. • ISR66313: L1 and L2 operaror should not be able to 'Response' or 'Reset' alarm. EXCEL 5000 Direct and EXCEL 5000 Scan Task • PCR 1-660FS: Memory leak is observed in SALT when 650 points are put in scan. • PCR 1-670H9: BNA time is not set to current system time with two C-Bus channels. EXCEL 5000 Direct Dialup • ISR66384: Trend gaps are appearing at semi-regular intervals. The gaps vary in length and vary in which point has them. Installation • ISR66729: The Logger service is not installing on a standalone Lonworks Point Server upgrade. Point Servers • ISR68998: gdanotcli.exe exception occurs when processing notification with null szCondition field. 10 www.honeywell.com Problems resolved in HMIWeb Station and Display Builder R3.5 Build 390 This section provides an overview of the problems resolved since Station and HMIWeb Display Builder R3.5 Build 361 was released with SymmetrE R310.1. Internal System Report (ISR) numbers are also provided. • ISR66573: In some cases Station print preview displays two pages. • ISR67411: Sometimes when you select an alphanumeric and start typing, the text goes to the command zone. • ISR67499: The Station OK and Cancel buttons on the logon dialog box are not localized. • ISR67629: Combo box contents in the toolbar of Station are not localized. • ISR67775: A character is lost when typing into an alphanumeric which sets the value of another alphanumeric. • ISR67826: Gradient fill isn't drawn on some printers. • ISR67893: Some display pages will generate a lot of unnecessary errors in the log. Problems resolved in SymmetrE Web Server R3.5 Build 390 This section provides an overview of the problems resolved since SymmetrE Web Server R3.5 Build 361 was released with SymmetrE R310.1. Internal System Report (ISR) numbers are also provided. • ISR66651: Accessing the Weekly Schedule tab of a BACnet Schedule Object point detail display from SymmetrE Web Server can result in a browser crash. • ISR67091: There are 2 instances of HW_LoggingServer.exe running on the server, causing log files not to be rolled over. • ISR67276: window.external.logmessage doesn't work when a page is loaded in the browser. • ISR67481: The Mandatory Upgrade page is displayed in the browser when connecting to an SymmetrE Server with SymmetrE Web Server "Upgrade Version" greater than 1.0.0. • ISR68051: Cannot print DSP pages from SymmetrE Web Server. Problems resolved in Quick Builder R2.30 Build 1131 This section provides an overview of the problems resolved since Quick Builder R2.30 Build 1031 was released with SymmetrE R310.1. Internal System Report (ISR) numbers are also provided. • ISR62330: Launching QB generates an Access Error. QB operates normally afterwards. • ISR66501: Issues with OPC import Wizard property mapping. • ISR66619: State descriptors are reversed for EXCEL 5000 scan task status points imported via the QB EXCEL 5000 Discovery Wizard. • ISR67054: Quick Builder does not upload the correct alarm limit values for an EXCEL 5000 Scan Task point if these values contain ‘,’ decimal separators. • ISR69475: Algos are lost when copying points from Excel to Quick Builder. • ISR69632: EXCEL 5000 Discovery Wizard removes the umlaut letters ä or ö if they have been used. • ISR70237: Quick Builder CARE RTF import wizard for EXCEL 5000 Scan Task does not correctly import the point state descriptors. • ISR70297: Point descriptors that are assigned in CARE are not getting imported to QB using CARE/XLToolkit import wizard for XL500 points. www.honeywell.com 11 Appendices Appendix A – ActiveX controls embedded in DSP and HMIWeb display pages A recent update to Microsoft's Internet Explorer browser affects the way users interact with ActiveX controls embedded on DSP displays and HMIWeb displays (as well as any other HTML pages). This update will require ActiveX controls embedded on display pages to be "activated" before they can be interacted with. Controls can be activated by either left-clicking them with the mouse, or tabbing until the selection rectangle appears around the object and then pressing the space bar. This change in behavior will only affect SymmetrE Web Server, which uses Microsoft Internet Explorer. Affected operating systems are Windows XP. System displays have been modified to prevent this behavior but custom displays may experience this behavior. More information on the update can be found at: http://support.microsoft.com/kb/912945/. 12 www.honeywell.com