Fluidized Bed Thermal Oil Heater
Fluidized Bed Thermal Oil Heater using coal, rice husk, palm shell, wood waste, or other biomass.
Shared by: nodhi
fluidized bed coal fired thermal oil heater VTF 1 clean coal technology basuki heater Coal is widely available and cheap fuel for industries. We offer highly efficient Thermal Oil Heater using bituminous coal as fuel. Now you can get the advantage of the low cost coal to run your process. Basuki Thermal Oil Heater offer a complete range of clean coal technology covering fuel handling, fluid bed combustor, ash removal and air pollution control system. Standard models with capacity from 400,000 kcal/hr to 6,000,000 kcal/hr, using variety of solid fuels. Other capacity are available on request. 2 clean coal technology basuki heater using latest coal firing technology • Fluidized bed combustion is undoubtedly one of the most attractive means of burning coal due to its various advantages. Basuki coal fired thermal oil heater consist of a coil type heat exchanger located above a fluid bed furnace. Coal is burnt in a fluidized bed combustor. This produces minimum pollution and can ensure complete combustion of the fuel. fluidized bed combustor can burn a variety of solid fuels such as wood waste, rice husk, palm shell and coal in same unit. Effective mixing of fuel and air in the reactor makes it possible to obtain complete combustion with less excess air. • Fluid bed combustion and effective secondary air distribution results in complete combustion of coal and produces less carbon monoxide (CO) and almost white smoke. Due to low temperature operation of the fluid bed combustor ( about 800 – 900 C) low amount of NOx is produced by avoiding oxidation of nitrogen compounds contained in the coal. For high sulfur fuels, it is possible to trap the sulfur in the bed and avoid costly de-sulfurisation equipment. Higher thermal efficiency can be obtained using bituminous coal due to low excess air and low stack temperature. 3 clean coal technology basuki boiler using latest coal firing technology Low Operation Cost Cheaper coal fines used as fuel, size of coal required is 100 % below 15 mm. Fuel Flexibility 100 % capacity of the boiler can be obtained with nearly all types of coals. No capacity reduction for lower heating value. Low Maintenance Cost Very reliable as the only moving part is the fans which are outside the hot zone. 4 latest development in control system Programmable Logic Controller (PLC) 5 latest development in control system Full Color LCD Touch Screen Control & Display System MIMIC DIAGRAM INDICATOR DAILY REPORT GRAPHIC DIAGRAM 6 other advantages of thermal oil system Low Operating Pressure Thermal Oil systems operate at a maximum system pressure of 5 barg and can supply hot fluid at temperature up to 300 C. A hot water or steam system for this temperature will operate at higher than 60 bar pressure. Higher System Efficiency Thermal Oil heating systems give higher thermal efficiency than steam systems as there is no condensate loss. No Scale Formation or Corrosion The mineral oils used for the heating plant are non corrosive and are stable at the operating temperature. The heating plant can operate for long time (8 – 10 years) without needing change of fluid or system cleaning for scale, corrosion, etc. 7 other advantages of thermal oil system Low Maintenance Cost Thermal oil plants require lesser maintenance due to the closed loop operation and simple construction. Fully Automatic The entire heating plant from fuel storage, feeding, combustion and the oil circuit operates automatically to give continuous supply of hot heat transfer fluid to the process. There are adequate safeties to ensure a safe and reliable operation. No Need of Softener Thermal oil systems do not need equipment like softeners as required for water or steam system. 8 capacity selection BASUKI can design, supply, and erect thermal oil heating plants of capacity from 400,000 kcal/hr to 6,000,000 kcal/hr, using variety of solid fuels. Other capacity are available on request. Standard models of BASUKI Coal-fired Thermal Oil Heater - VTF Description U/M VTF-04 VTF-06 VTF-10 VTF-15 VTF-20 VTF-25 VTF-30 VTF-40 VTF-50 VTF-60 THERMAL CAPACITY kcal/hr 400,000 600,000 1,000,000 1,500,000 2,000,000 2,500,000 3,000,000 4,000,000 5,000,000 6,000,000 Thermal Oil Flow Rate m3/hr 28 42 70 105 140 175 210 280 350 420 Maximum oil temperature 300 C 300 C 300 ºC 300 ºC 300 ºC 300 ºC 300 ºC 300 ºC 300 ºC 300 ºC 300 ºC Temperature rise 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC 30 ºC Inlet/Outlet Header size DN 65 80 100 150 150 150 150 200 250 250 Coal consumption *) kg/hr 87 130 217 325 433 542 650 867 1,083 1,300 Oil content of coil liter 400 650 1,050 1,300 2,100 2,300 3,750 4,400 7,350 7,400 Chimney; Diameter mm 320 400 500 600 700 800 900 1,000 1,100 1,200 Height m 20 20 20 20 20 20 20 20 20 20 Overal dimension; Furnace Height ( H2 ) mm 2,619 3,193 3,917 4,279 5,929 5,281 6,305 6,850 7,455 8,402 Diameter ( D ) mm 1,613 1,804 2,176 2,404 2,736 2,972 3,176 3,372 3,772 3,973 Overal dimension; Coil assembly Diameter ( D ) mm 1,613 1,804 2,176 2,404 2,736 2,972 3,176 3,372 3,772 3,973 Height ( H1 ) mm 1,500 1,500 1,500 2,000 2,000 2,500 2,500 2,500 2,550 2,550 Total transportation weight; Furnace ( 1 ) kgs 3,434 3,841 6,753 5,118 9,325 9,010 12,899 13,243 16,013 18,159 Coil ( 2 ) kgs 2,003 4,283 6,580 7,936 10,931 12,584 17,414 20,043 28,361 34,127 *) Based on Gross Calorific Value (As Received) of coal 6,500 kcal/kg. Minimum acceptable Gross Calorific Value (As Received) of Coal 3,500 kcal/kg PT BASUKI PRATAMA ENGINEERING Head Office & Factory Jl. Pulo Lentut No.2 Kawasan Industri Pulogadung Jakarta 13920 - Indonesia Tel. (62-21) 460 3212 Fax. (62-21) 460 3220 www.basuki.com firstname.lastname@example.org 05-2009