VALVES Wherever there is a danger from foul water backing up into a property through the drainage system the valve will close automatically to prevent ﬂood damage. Forge valves have now been used to protect many basement ﬂats and low lying properties previously affected by foul and combined sewers unable to cope with abnormal weather conditions. The valve is manufactured in Britain from polypropylene, which makes it light enough for one man to lift and is simple to install and maintain. VALVES FEATURES The Forge Valve is ﬂoat operated forcing a closure of the pipe when backﬂow occurs. Increased backﬂow pressure on the ﬂap forces it tighter closed. The valves are light and can easily be carried into awkward places. No tools are required to remove the lid and gloved hands can easily remove the wing nuts. The seal between lid and valve body is designed for life and will not need to be replaced when the valve is opened. Float and ﬂap assembly lift out with gloved hand once lid is removed. No tools required. Lid bolts remain attached to valve body when wing nuts are removed. The valve is made from polypropylene which is extremely durable and resistant to chemicals. This smooth material resists the build up of fat and can easily be cleaned with a hose. The air release valve ensures a quick reaction to rising water levels. Available from stock with prompt delivery to suit pipe diameters of 100 mm, 150 mm, 225 mm and 300 mm, other diameters can be manufactured to special order. VALVES DIMENSIONS B B C A A SEWER VALVE SIDE VIEW DIA 100mm 150mm 225mm 300mm DOMESTIC 100MM DOMESTIC VALVE SIDE VIEW B C 365mm 415mm 500mm 560mm 370mm WIDTH 420mm 450mm 600mm 710mm 500mm WEIGHT 13.0kg 14.0kg 22.0kg 31.0kg 12.0kg A 265mm 315mm 400mm 460mm 270mm 490mm 540mm 690mm 810mm 500mm VALVES FITTING INSTRUCTIONS On receipt of your valve please check that it has not been damaged in transit. The ﬂap/spindle assembly should swing freely from the pivot points and this may be checked by touch through the outlet pipe. Attach the air release valve by screwing onto the thread on the lid. The lid is marked with an arrow which should align with the normal ﬂow through the pipe. It is best to install the valve in a purpose built inspection chamber so that access can be made to it to remove the lid, wash down and inspect. A minimum of 600 mm by 750 mm sized chamber of precast concrete sections or engineering brickwork would allow enough space around a 100 mm or 150 mm dia valve. Larger valves are best suited in concrete rings. A good no-nonsense web site for precast concrete sections is www.hepworthconcrete.co.uk . The Domestic type valve does not need to be housed in a purpose built chamber. If the depth from ground to invert level is less than 1.0m it will be accessible by ﬁtting UPVC raising sections (available from your builders merchant) of standard 500 mm diameter. These clip to the valve casing and can be surrounded with granular material or lean concrete. You will need Flexseal or equivalent couplings and possibly bushes to attach the valve to the sewer pipe. As you tighten the coupling it is important that you check that invert of valve and pipe are correctly aligned. We have included a brief list of couplings but for more detailed information visit www.ﬂexseal.co.uk . We recommend that the valve is checked at least twice a year. All that is needed is a quick clean with a high pressure hose. VALVES FITTING SPARE PARTS Spare parts are available should they be needed but they do need to be ﬁtted by a competent person who has read these instructions. The existing ﬂoat/ﬂap assembly can be removed in one unit by lifting out of the pivot cradles. Remove the neoprene rubber from the spigot end of the incoming pipe only if it is damaged by loosening the screw on the retaining band. “Don’t ﬁx wot ain’t broke”, its easier to leave the ﬂap sealing rubber in place if it is undamaged than change it in a cramped manhole. The seal is designed for the life of the valve. The new pivot rod may need to be cut shorter to prevent it binding against the side walls of the valve. Each valve is hand made so we leave the pivot rod long to accommodate any small differences between valves. Use the old ﬂap assembly as a template, when inserted the ﬂap must seat directly over the rubber seal NOT to one side. This may mean removing a little from each end of the pivot rod. check it will turn freely in the cradles. If you are replacing the rubber seal, clean pipe end and ﬁt new rubber seal and retaining band but do not fully tighten or push fully onto pipe. Now replace ﬂap assembly and gently close ﬂap pushing rubber seal into place and ensuring a continuous seal between ﬂap and rubber seal. Now tighten retaining band. All that's left is to secure the ﬂoat onto the spindle using the two screws provided. Hold the ﬂap closed with one hand and centralise the ﬂoat with the other. Position it slightly below the top of the side walls to avoid it clashing with the lid. Mark his position and ﬁx. The self locking bolt attaching the ﬂap should be left loose enough to allow some movement. VALVES FLEXSEAL VALVE COUPLINGS PIPE DIAMETER AND TYPE 100mm 100mm 100mm 4” S.G.W. 160mm 150mm 150mm 150mm 6” S.G.W. 150mm Cast Iron, UPVC, Osma, Hunter, etc Stainless Hepworth Supersleve, Naylor S.G.W. Vitriﬁed Clay, Pitched Fibre, Asbestos cement. UPVC, Osma, Hunter, etc Cast Iron, Stainless, Ultrarib Hepworth Supersleve, Naylor Densleve Asbestos Cement, Pitch Fibre Salt Glave Ware Concrete up to 200mm OD COUPLING SC115 or SC120 SC115 or SC120 SC120 SC137 SC175 or SC120 SC175 or SC120 SC180 SC200 SC200 SC200 BC16/160 BC16/160 BC08/160 BC08/115 BUSH VALVES PRESSURE PLATE The Forge sealed Manhole Pressure Plate has been designed as a low cost measure to:prevent nuisance caused by smells prevent leakage of sewage from manhole covers improve health and safety with deep manholes. The sealed pressure plate has been designed for use with 600 mm by 600 mm manhole covers where it may be bolted to the underside of the frame or used as a separate ﬁxture and built into the seating brickwork. The sealing plate is manufactured from polypropylene which is resistant to corrosion by chemicals and sewer gasses. The removable plate is held ﬁrmly in position to its sub frame with eight stainless steel wing nuts which only need to be hand tightened to ensure an effective seal. The integral double neoprene seal will prevent efﬂuent or gasses being expelled. The plate enables the clear display of warning notices regarding manhole depth or “permit to work” situations. Thus highlighting danger at the point of entry and avoiding exposure of workers to unnecessary risk. VALVES FITTING PRESSURE PLATE To ﬁt pressure plate:1. Remove the existing 600 mm square manhole cover and frame. 2. Increase the existing bedding depth by 30 mm to allow for the thickness of the pressure plate. 3. Bed pressure plate in bedding mortar then bed manhole frame on top or attach pressure plate to manhole frame with bolts and then place on mortar bed. 4. If preferred the pressure plate can be built into the manhole shaft brickwork.
Pages to are hidden for
"VALVES"Please download to view full document