VIEWS: 3 PAGES: 1 POSTED ON: 4/16/2012
M1602.4 Balanced return air. Restricted return air occurs FLORIDA BUILDING CODE in buildings when returns are located in central zones and closed interior doors impede air flow to the return BALANCED AIR CERTIFICATION grill or when ceiling spaces are used as return plenums and fire walls restrict air movement from one portion of I attest the interior airflow was tested for pressure the return plenum to another. Provisions shall be made in differentials across interior closed doors of habitable residential buildings to avoid unbalanced air flows and rooms where returns are centrally located. The test results pressure differentials caused by restricted return air. showed pressure differential was limited to 0.01 inch WC Pressure differentials across closed doors where returns (2.5 Pa) or less at each location. are centrally located shall be limited to 0.01 inch WC (2.5 Pa) or less. Pressure differentials across fire walls in ceiling space plenums shall be limited to 0.01 inch WC (2.5 Pa) Date Signature by providing air duct pathways or air transfer pathways from the high pressure zone to the low zone. 1. Transfer ducts may achieve this by increasing the License # Printed Name return transfer one and one half times the cross sectional area (square inches) of the supply duct Building Permit: entering the room or space it's serving and the door having at least an unrestricted 1 inch (25 Mechanical Permit: mm) undercut to achieve proper return air balance. Job Address: 2. Transfer grilles shall use 50 square inches (4.6 mm) (of grille area) to 100 cfm (0.05 m3 /s) (of supply air) for sizing through-the-wall transfer grilles and using an unrestricted 1-inch (25 mm) undercutting Complete this form and post it in a of doors to achieve proper return air balance prominent location near the air handler or 3. Habitable rooms only shall be required to meet these requirements for proper balanced return air furnace. A Certificate of Occupancy will excluding bathrooms, closets, storage rooms and laundry not be issued until the form is posted on rooms, except that all supply air into the the job. master suite shall be included.
Pages to are hidden for
"Mechanical Balanced Air Certification"Please download to view full document